Bay Heating & Air Conditioning has been servicing the heating and air conditioning needs of Avon OH since 1944.
Call us now at: 440-249-0500 or check out the reviews and testimonials from your neighbors, that make us the top rated service provider in Avon OH.
for Avon, OH
Our Reviews by City
On time and efficient
Mckendry - Avon, OH
Professional and knowledgeable
Reed - Avon, OH
Great Service, Awesome Price!
Houghton - Avon, OH
Service was great.
Very knowledgeable and courteous!
Griffiths - Avon, OH
Reilly - Avon, OH
Your technician was knowledgeable and personable
Great customer service. John, Jerry and Antonio were above and beyond any service tech we have ever had to our house in 20 years! A+ work from laying
Schurch - Avon, OH
Best service experience we have ever had. We started with Paul quoting the job—He was very informative and professional. The crew that installed was exceptional-John,Jerry and Antonio. High quality work and exceptional communication.
Prompt. Professional, and courteous.
Rozzo - Avon, OH
Jason is the best.
A/C Tune Up
Conrad - Avon, OH
Jason is very knowledgeable and personable. Great customer service.
Stinard - Avon, OH
Great technician, friendly, knowledgable, and efficient.
LuliRoger - Avon, OH
I have been a customer of Bay Furnace for many years and have never been dissatisfied.
Great service,good price, would hire again.
Barrett Phyllis - Avon, OH
Brian the technician explained everything and suggested we should consider joining their annual maintenance because of the age of our furnace and air conditioning. He also explained
Always a pleasure having such professional people to deal with !!!
KonopkaKathy - Avon, OH
Fisher - Avon, OH
Technicians were efficient and pleasant.
Great S ervice. Great service people
RockValerie - Avon, OH
Jose has been servicing my furnace and air conditioner for maney years he is great
very experienced and professional and polite
Hazinakis - Avon, OH
I checked the refrigerant charge at 3 degrees of superheat. This may be due to leak stop additives. I also checked condensate drain and flow. I removed cap due to long run times causing the pan to hold water. System is operational at this time. Due to refrigerant loss and type of refrigerant i highly recommend replacement.
Return and replace two thermostats for warehouse tube heaters
Found board on outdoor unit had failed. Replaced with new board and paired to furnace. Unit operational.
No Cooling. Found A Bad Reading 0+0+370 Dual Run Cap @ 45+5+370 Dual Run Cap, Cycled Unit Fine At This Time.
A/C tuneup complete, flushed drain, filter was clean coustomer provided, turned off bypass humidifier for the season, hosed down condenser coil, checked capacitor/compressor/contacter, all electrical connections are secure, cycled cooling with ok operation. Thanks johnathan
Checked Thermostat. Flushed AC trap with water. Checked filter. Checked all electrical connections. Checked contactor. Checked capacitor. Cleaned outdoor coil with water. Cycled system to check. System is operating properly at this time
Found Existing five wire was ran during new install two outdoor unit from indoor unit. Added a third wire for communication fault to be removed. Cycled system to check. System is operating properly at this time. Thanks Brian.
Found Outdoor unit to be dirty. Clean coil. Removed indoor filter. Indoor system is frozen. I had to run the heat to melt the coil. After testing the charge I found the indoor coil to be freezing in the outdoor coil to be boiling. Signs of a bad TXV. I release some of the charge and got it to be at 8:33Â° indoor coil for temporary cooling. Customer has quotes on TXV and replacement. Will get back to us with a decision soon. System is operating but not properly at this time. Thanks Brian
A/C tuneup complete, shut off fan power humidifier for the season, flushed drain, filter was clean customer provided, hosed down condenser coil, checked compressor/contacter/capacitor, all electrical connections are secure, cycled cooling with ok operation. Thanks johnathan
Added leak seal. System is operating properly at this time. Thanks Brian
No cooling. I found a failed capacitor and a blown fuse. I replaced both and cycled with proper operation.
Customer said temperature was not dropped from thermostat. Cycle unit found system was running at 54* evaporators coil. Trying to take change out to 45* coil or 5* superheat but was not getting there. At times of dispatch unit is working at 10* temperature difference. Supply air 64 and return air 74*. Would call if needed and estimate.
I replace the failed blower motor and capacitor. I replaced the number 35 water panel. I cycled the unit with proper operation.
Found outdoor unit dirty. Clean coil. Checked refrigerant charge . Found system to be slightly over charge. Remove refrigerant until 12Â° sub cooling. 11Â° sub cooling required. Cycled system to check. System operating properly at this time.
A/C tuneup complete, replace capacitor, flushed drain, shut off bypass humidifier for the season, hosed down condenser coil, checked capacitor/compressor/contacter, all electrical connections are secure, cycled cooling with ok operation. Thanks johnathan
Unit is making a loud noise. I found the bearings on the motor are failing. We quoted $621.00 for the motor replacement. And it is scheduled for tomorrow between 9:00-12:00. Bring #35 water panel.
Found Condensing fan motor was out of balance and had caused the frame to where the motor boats to to crack. Explain to customer of the cost of repair is not worth it and recommended replacing the system due to age and condition. Customer agreed. I gave customer two quotes on carrier equipment. Customer would like to look at them and get back to us. System is not operating at this time. Thanks Brian
Call back from Brian Customer said unit freezes up. Hook gage on found Unit was low on charge. Charged up to 35* coil. Supply air 57* return air 72*. Note I have add 2 lbs or r 22. At times of dispatch unit is working at a temperature difference of 15*.
Upon arriving cycled unit on. Found that blower motor did not kick on. Found was a fail capacitor. Replace capacitor 40mfd with turbo 200. Also wanted to schedule an estimate for a zoning system.
No Cooling. At My Arrival Found R-22 Unit Low On Charge Add 4lb R-22 And Super Seal. Required Subcooling 10*, Liquid Pressure 210, Liquid Line Temp 95*, Cycled Unit Fine At This Time.
Thermostat is showing excessive static pressure codes. Need to speak with Jim price. System is operating properly at this time. Thanks Brian.
Found system low on r 22 refrigerant. Added 5 lbs r22. Cycled system to check. System is operating properly at this time. Thanks Brian
$119.95 A/C Tuneup. Replace #20x25x5 Air Filter. T-Stat, 65*-46*=20*D-T, Bypass Humidifier Turn Off And Damper Close Need #10Wp Trap Is , Blower Motor, R410A, Electrical, 80* Outside, Hose Down, Remove Leaves And Cottonwood, Cycled Unit, Clean And Check.
Check thermostat check blower motor change filter customer supply flush condensate drain. Turn Humidifier off. Supply air 55* return air 73*. Check disconnect 30 amps Fuse cycle unit on to check compressor and fan motor working. Wash and clean condenser coil. Outdoor temperature is 81*. At time of dispatch unit is working.