Bay Heating & Air Conditioning has been servicing the heating and air conditioning needs of Avon OH since 1944.
Call us now at: 440-249-0500 or check out the reviews and testimonials from your neighbors, that make us the top rated service provider in Avon OH.
for Avon, OH
Our Reviews by City
Service is ALWAYS A1 !!!
Konopka, Kathy - Avon, OH
Justin & his work ethics, are ABOVE & BEYOND. Always pleasant & concerned for his customers wellbeing !!!
Service was done in a timely fashion
Hazinakis - Avon, OH
We have always used Bay Heating and would highly recommend their service.
Great S ervice. Great service people
RockValerie - Avon, OH
Jose is very knowledgeable, polite and an all around fabulous sergvice person.
Great 1st Experience
Jim - Avon, OH
Was very impressed with the tenacity responsiveness and knowledge of fixing our problems. Great organization quality service very very happy
Great Service! Jason is wonderful!
PorterMarcia - Avon, OH
Fisher - Avon, OH
Our technician was prompt, efficient, neat appearance, courteous, polite, and knowledgeable.
Great service ... ALWAYS !!!
KonopkaKathy - Avon, OH
All these guys are great, but Jason … YOU ROCK my friend !!! Very knowledgeable, friendly and professional, things you don't find much anymore !!!
Fall Furnace Check
Conrad - Avon, OH
Jason is extremely knowledgeable of his work and very pleasant to talk with.
Jim was very professional and explained our new system
WalshFrank - Avon, OH
We had a couple prices. Bay was very competitive tho not the lowest. We had Carrier for 20 years and decided to continue with the product. Bay was recommended as the contractor to choose for Carrier products.
EXCELLENT, EFFICIENT service on a SUNDAY no less!
Lewis - Avon, OH
Came out on a Sunday. Tech diagnosed problem very quickly, and HAD the necessary part with him. Had us up and running in less than 1/2 hour. We will never call anyone else after our experience today.
Hannes - Avon, OH
Prusinoski - Avon, OH
Justin listened and explained things which many of the techs don’t do
On time. Was quite quick. Professional
Blume - Avon, OH
Fisher - Avon, OH
Quick and efficient service
Great service !!!
KonopkaKathy - Avon, OH
Justin is very professional. He explained everything he did, and left no stone unturned. Very thorough, and friendly, great customer relations !!! We always feel confident and worry free, after he checks everything out !!!
Unit making noise. Found plenum to be tin canning. Recommended attaching some drives to help prevent noise. Customer would not like to repair at this time. Cycled furnace from tstat with proper ok operation at this time.
Found garage heater ignition module bad will need replaced also Arzel zoning board bad will also need replaced customer has April air humidifier with leaking feed tube and water panel in very poor shape will need feed tube and water panel for number 700 April air humidifier office to call with Priceing. Also customer would like arzel zone panel moved to wall approximately 5 feet away as it is currently mounted under a leaking humidifier approximately 1 1/2 hours to move.
Furnace tuneup complete. Replaced plugged filter provided by customer. Inspected and cleaned hsi, flame, burners, inducer, blower, cap, controls, safeties and cabinet. All electrical connections are secure. Inducer motor is a little noisy but operating ok at this time. Replaced blower run cap that was outside operating limits and inducer fan that was cracked. Ran furnace from tstat with ok operation at this time. Tstat reset. Recommend annual maintenance of all equipment and replacing air filter every 30-60 days.
Water leak. I found water leaking at a 45 elbow on the 3â€ furnace exhaust. I sealed with pvc cement. If the leak reappears we would need to replace part of the exhaust and possibly replace the bay vent termination kit.
Found noisy bearings on inducer motor. Replaced motor, gaskets, blower wheel, rubber grommets and fan wheel. Cycled with ok operation at this time. Reset tstat.
Clean out furnace drain trap Unit was coding on error code 32. I found the drain trap was plugged. I removed and cleaned out the drain trap. I cycled the furnace with proper operation.
$119.95 Furnace Tuneup. Replace Car-0909Wp. T-Stat, 16 Ohms H.S.I. Flame Sensor, 2-Stage 90% Inducer, Electrical, 1.7â€ & 3.5â€ W.C. Gas Valve, Burner, Drain Trap, 5+370 Run Cap Blower Motor, 54* & Rain Outside, â€œHumidifierâ€ Hum-Stat, Fan Power, Scale Control Insert, Drip Tray, Water Valve, Solenoid, Electrical, Drainline, Cycled Unit Clean And Check.
I replaced and tested the gas valve, Orifices and manifold. The system is operating properly at this time . PO#28236.
Tuneups complete. Air filter is clean. Inspected and cleaned hsi, flame sensor, burners, inducer, gas valve, safeties, zone controls, blower, cap and cabinets. Replaced blower motor run capacitor that was outside operating limits. All electrical connections are secure. cycled furnace from both zones with ok operation at this time. Tstats reset. Humidifier cleaned, cycled, water panel replaced, bypass opened, and humidistat set.
Furnace tuneup complete. Replaced air filter provided by customer. Checked tstat batteries. Inspected and cleaned hsi (74ohms), flame sensor, inducers, blower , cap, cabinets, controls, safeties, and all electrical connections secured. Delta t was high upon arrival. Opened all supply air registers that were closed in basement and visually inspected all SA and ra registers on both floors to Assure proper air flow. Delta t is now within factory operating limits. Delta t=68 degrees. Cycled furnace from tstat with ok operation at this time. Reset tstat. Highly recommend leaving ALL supply air registers open during heating season.
No heat. I found the system with dead and corroded thermostat batteries. I cleaned the terminals and replaced the batteries with the coustomers supply. I cycled the furnace with proper operation.
Coustomer had concerns about the humidity readings. I found the infinity control was off so I adjusted the offset up by 10%. Water flow was an issue so I turned down water pressure to the solenoid valve. Furnace run time was too long for her so I put the furnace control board in control of staging. I set humidity level to medium. I explained the dehumidification mode of the ac and the reason for over cooling. I adjusted cooling humidity from 52% to 54%. The homeowner has notes and a better understanding of the equipment operation.
Heating tune up.
Club Furnace And Humidifier Tuneup. Replace #401Sg. T-Stat, 18 Ohms H.S.I. Flame Sensor, 2-Stage 90% Inducer, Electrical, 1.7â€ & 3.5â€ W.C. Gas Valve, Drain Trap, 5+3370 Run Cap Downflow Blower Motor, 56* Outside, Cycled Unit Clean And Check. â€œHumidifierâ€ Hum-Stat, Bypass Damper Open, Scale Control Insert, Electrical, #35Wp, Drainline, Cycled Unit Clean And Check.
Found heat exchanger plugged. Unit needs replaced. Office to call tomorrow to schedule estimate, after office hours now.
I replaced the rusted burners and cycled the furnace. THe flames would not carry past the first burner. I removed the orifices and found rust and rusty sludge in the manifold and orifices. I cleaned the orifices and cleared the manifold with CO2. I was able to cycle the furnace to test components. Unit is operational. However the manifold, orifices and gas valve need replacement due to moisture damage.
No Heat. Found Rust Burner Need Replace
No Heat. Found Limit Trap, Plug #14x25x1 Air Filter Replace Supplied, Bad Run Cap Reading 8.45+370 @ 10+370 Replace, Cycled Unit Fine At This Time.
Perform furnace tune up cycled to check operation all okay at this time replaced filter and checked water panel all okay.
Water is leaking. I found a blocked condensate trap. I cleared the drain trap with 300psig of CO2. The system flushed out and is draining freely. I sealed the access point and the ac is operational.
Tuneups complete. Replaced air filter and tstat batteries provided by customer. Inspected and cleaned hsi, flame sensor, burners, inducer, blower, controls, safeties, and cabinets. All electrical connections are secure. Cycled clef heat from tstat with ok operation at this time. Tstat set to the way it was found. Humidifier was installed by us recently and found to be leaking. Cleaned, cycled , Replaced water panel, and adjusted the water flow that was wide open. No leaks present at this time. Set humidistat to 35%. Caregiver was only one available so I had to direct bill customer.
Clean burners flame sensor vestibule and controls check all operating and safety controls check blower motor and filter fire furnace to check OK check humidifier water panel and operation OK
Club Furnace And Humidifier Tuneup. Replace #35Wp. â€œFurnaceâ€ T-Stat, 60 Ohms H.S.I, Flame Sensor, 80% Inducer, Electrical, 3.5â€ W.C. Gas Valve, Burner, 7.5+370 Run Cap Blower Motor, #16x25x1 Air Filter, Cycled Unit Clean And Check. â€œHumidifierâ€ Automatic Hum-Stat, Scale Control Insert, Electrical, Drainline, Open Damper, Cycled Unit Clean And Check.
No cooling. I found the system with no refrigerant charge. System is being pulled into a vacuum by the compressor. Due to age, ineffency and condition system should be replaced.
Perform furnace tune up cycled to check operation all okay at this time.