Bay Heating & Air Conditioning has been servicing the heating and air conditioning needs of Westlake OH since 1944.
Air Conditioning Repairs & Air Conditioner Replacements, Heating Repairs & Furnace Replacements and much more!
Call us now at: 440-249-0500 or check out the reviews and testimonials from your neighbors, that make us the top rated service provider in Westlake OH.
for Westlake, OH
Our Reviews by City
Nilsson - Westlake, OH
Marty is the consummate service person for Bay Furnace. I always request him if available for my air conditioner / furnace annual inspections.
Star - Westlake, OH
quick and no problems
Grane - Westlake, OH
Lee - Westlake, OH
Jose is professional and efficient. Always a positive experience.
Loehr - Westlake, OH
Installation of new system
Angell - Westlake, OH
Everything from the first contact with the after hours emergency technician to the follow up diagnostic call to the conversation with the sales team was very professional. The installation team was efficient, friendly, knowledgable and thorough. I highly recommend Bay Furnace for your heating and cooling needs. For more than 20 years we have utilized their services and have absolutely no complaints.
very happy with the experience
Clark - Westlake, OH
Quick assessment of Cooling / Air Conditioning Unit
Mcdonald - Westlake, OH
Excellent professional demeanor and showed knowledge & expertise in area of the cooling mechanism of the A.C. unit. Jose was concerned and offered me several options to consider for dealing with the problems of the A.C. unit. He was very professional.
Ormsby - Westlake, OH
Ormsby - Westlake, OH
Very knowledgeable people working in customer service and on the road.
Ormsby - Westlake, OH
Jose was awsome
Sue - Westlake, OH
Manco - Westlake, OH
Knows what he is doing
worked on one of the hottest days of the year - great service
Pat Costello - Westlake, OH
Greenspan - Westlake, OH
Service was excellent, as always. Your technician was very professional
Club Furnace And Humidifier. Replace #12Wp. T-Stat, 60 Ohms HSI, Flame Sensor, 90% Inducer Assembly, 3.5â€ W.C. Gas Valve, Drain Trap, #20x25x5 Air Filter, Electrical, 76* Outside 10+370 Run Cap Blower Motor, â€œHumidifier â€œ Hum-Stat, Bypass Open, Water Valve, Solenoid, Feed Tube, Electrical, Drainline, Cycled Unit, Clean And Check.
Club Furnace And Humidifier Tuneup. Replace #35Wp. T-Stat, Spark Igniter, Flame Sensor, 4+370 Run Cap 90% Inducer Assembly, 3.5â€ W.C Gas Valve, Burner, Drain Trap, 15+370 Run Cap Blower Motor, 71* Outside, â€œHumidifierâ€ Hum-Stat, Fan Power, Scale Control Insert, Water Valve, Solenoid, Feed Tube, Drainline, Cycled Units, Clean And Check.
Unit 1 Check thermostat check blower check humidifier change filter check hot service ignition 85 ohms. Cycle unit on to check all other components on unit. All others information please check heating Tuneup form. At time of dispatch unit is working. Outdoor temperature is 66* Unit 2 Check thermostat check blower change filter check hot service ignition 49 ohms. Cycle unit on to check all other components on unit. All other information please check heating Tuneup second unit form. At time of dispatch unit is working. Outdoor temperature is 66*.
Clean burners flame sensor condensate trap vestibule and controls change humidifier water panel and filter check all operating and safety controls fire furnace to check low and high fire
Unit Making Noise. Found 220 Line Reading 346 From Breaker Box, Owner Will Electric Company.
Water leaking. I cleaned the condensate trap with CO2.;I cycled with proper operation.
Club Furnace And Humidifier Tuneup. Replace #201Sg. Bypass Humidifier Not Used. T-Stat, 56 Ohms HSI, Flame Sensor, 2-Stage 90% Inducer Assembly, 1.5â€ & 3.5â€ W.C. Gas Valve, Drain Trap, Electrical, 132* & 122*-72*=60* & 50* T-R, V.S Blower Motor, 73* Outside, Cycled Unit, Clean And Check.
Heating tune up.
Connected control to new wifi.
His budget was a lower than what we could offer.
Replace thermostat and module. Parts were replaced and the unit was cycled with proper operation.
2= Commercial Rooftop A/C Tuneup. Replace 2=#20x25x2 & 4=#16x16x2 Air Filter. 2=T-Stat, 74*-56*=18* & 74* & 62*=12* D-T, 2=Drain Trap, 2= Blower Motor, R-22 & R410A, 80* Outside, Cycled Units, Clean And Check.
No cooling. Repaired low voltage wire at condenser. Rodent chewed the wire. Cycled cooling from tstat with proper operation at this time. Reset tstat.
Follow up diagnosis repair. Replace contactor and insulting 1 ft of armor flex on suction line. At time of dispatch unit is working.
Customer said she feels the system is blowing warm air. Cycle unit on and found the outdoor unit isnâ€™t working. Check capacitor and found it was not reading. Replace capacitor with turbo 200x and cycle unit on to check compressor and fan motor working. At times of dispatch system is working.
Will call and discuss capping off registers in crawl space.
Club Furnace And Humidifier Tuneup. Replace #35Wp. T-Stat, 58 Ohms HSI, Flame Sensor, 2-Stage 90% Inducer Assembly, Drain Trap, Ez-Flex #20, V.S. Blower Motor, 75* Outside. Humidifier Fan Power, Hum-Stat, Scale Control Insert, Drip Tray, Feed Tube And Nozzle, Drainline, Water Valve, Cycled Unit, Clean And Check.
Found bad capacitor. Replaced parts system operating properly at this time. Recommend replacement of contactor. Thanks Brian. Bring ft of armorflex
Rental Property dealt with owner over the phone. Couldnt get budget out of Doug aka Mike. So I put together lowest and highest. He said we were double the price of the other 2 bids he received. He also wanted the equipment carried up the roof later instead of the crane that I had in the bid. I let him know that it was not only unsafe for our installers, but not safe for his new equipment.
Heating tune up. We found a failure of the #3 heat exchanger cell. The customer indicated that he will talk to Sean about furnace replacement. I advised the customer not to run the furnace due to possible hazardous CO production. The filter is extremely dirty and the customer stated that he will replace it this weekend.
System Leaking. Found A Plug Drainline And 2= Plug #20x25x1 Air Filter. Replace 2=#20x25x1 Air Filter And Cleanout Drain Trap With Co2, Cycled Unit Fine At This Time.
Call out to do a leak search search on unit 301. Found and verified Unit was leaking at the service Cap.
Checked blower motor and filter checked electric strip heat checked contactor capacitor compressor and fan cycle heat pump to check OK
Furnace Tuneup. Check thermostat check filter checked humidifier pad. Checked temperature difference. Cycle unit on to blower and inducers motor working. Complete the Tuneup form. At time of dispatch unit is working.