Bay Heating & Air Conditioning has been servicing the heating and air conditioning needs of Westlake OH since 1944.
Air Conditioning Repairs & Air Conditioner Replacements, Heating Repairs & Furnace Replacements and much more!
Call us now at: 440-249-0500 or check out the reviews and testimonials from your neighbors, that make us the top rated service provider in Westlake OH.
for Westlake, OH
Our Reviews by City
Keating - Westlake, OH
Prompt, courteous service
Star Metal Products Co - Westlake, OH
Bay Furnace Technicians are the best! they offer a time frame of when they will be coming, then they call and text to let you know they are on their w
Mcnamara - Westlake, OH
Gallagher - Westlake, OH
Good response and polite service person
DettorreSuzanne - Westlake, OH
Thankful for response on a Sunday, and fast return to let me know when he could arrive. Found problem immediately and had the right equipment on truck to get furnace up and running. Explained carefully how I could get the best cost and easy to pay by check.
Pickings - Westlake, OH
Brian, gray personaluty, knows his stuff.
Cable - Westlake, OH
tech was A-1
Eagle - Westlake, OH
Brian was very competent and explained what the problem was and the repair he made.
FeliceNancy - Westlake, OH
Timely and good
Rego - Westlake, OH
Very good service
Kelly - Westlake, OH
Marty is a great technician and is always able to correctly identify the problem and knows how to get it fixed.
Szarek - Westlake, OH
Jason was friendly and professional. He was well informed and I was very pleased with his service.
Review for Jose
MestekVicki - Westlake, OH
Jose provides amazing and thorough services. I was very happy to see that he was the technician assigned to my condo.
Bay Heating evaluation
Ohio George - Westlake, OH
On time and excellent service.
Good Service Price ?
Hammon - Westlake, OH
Found unit locked out due to open limit. Furnace had overheated due to dirty filter. Replaced filter and reset control board. Cycled system and system is operating properly at this time. Thanks Brian and Marty.
Found feed tube cracked, remove and replace, cycle to check, ok.
Furnace tuneup. Burner and blower compartments were inspected all safeties and connections were checked. Ignition sequence was cycled . Blower compartment and wheel were checked out. The system was cycled with proper operation. We replaced the filter with the customer supply. The furnace is in proper working order at this time.
Found bad ignitor. Replaced part. Cycled system and system is operating properly at this time. Thanks Brian.
$119.95 Heatpump Tuneup. T-Stat, #20x20x1 Air Filter, 5+370 Run Cap Downflow Blower Motor, R-22, R-Valve, Disconnect, Dual Run Cap, 36* Outside, Cycled Unit Fine At This Time.
Replace hot surface ignitor, cycle to check, ok
I called back multiple times and they said "they're still making a decision" the original estimate was at the end of January.
Intermittently Working. Upon arrival we found the water shut off to the humidifier. We open up the water and test cycle with proper operation. The reason for high water flow with humidistat was set too high. We explained operation and proper humidity levels to the customer. The system is currently operating correctly.
Blower Cold Air. Found Red Wire Disconnect From Transformer And Fan Limit Control Set To 50* Fan Off. Reconnect Red Wire To Transformer And Set 90* Fan Off. Cycled Unit Fine At This Time.
Return and remove splice from inside furnace cabinet to infinity control also replace humidifier drain line at no charge per Sean
Replace duo stat.
Replaced blower motor. Cycled system and system is operating properly at this time. Thanks Brian.
Found blower motor bad. Customer has agreed on repair.
Replaced fan control board. Cycled system and system is operating properly at this time. Thanks Brian.
Found ignition control bad replace. Replace control
Furnace inspection and cleaning. I cleaned the flame sensor, inspected the flame pattern. In the process of cleaning I did noticed water leaking from the exhaust coupling. I tightened the coupling which was loose and cycled the furnace with no more leaks. The humidifier water was turned off so I open the water set for 35% and cycled with proper operation. The filter was very dirty I replaced it with a 20x25x1 filter. The system is in good proper working order.
Found blower motor wheel to have been exploded. Also blower motor was faulty. Quoted customer on repair. Also quoted customer on new equipment. Customer is not prepared to make a decision at this time. Has paid for the $84 dollar diagnostic thank you.
Return and replace pressure relief valve cycle boiler to check OK
Found unit not sensing flame. Cleaned flame sensor. Cycled system operating properly at this time. Thanks Brian
Found feeder tube loose where it connects to the solenoid on the humidifier. This was dripping water on the floor. I tightened the connection and the leak has stopped. Thanks Brian.
Complete diagnostic from March 5, 2019 spoke with customer, tenant if he had to reset system again he said no it has been operating well.
Found relief valve leaking m335. If valve continues to leak, will need replaced. Estimate written.
No heat. Upon arrival I found the furnace operating properly. I cycled the furnace for 25 minutes with no fault or failures. I recommend scheduling a tuneup.
No Heat. Replace Variable Speed Motor Module, Cycled Unit Fine At This Time.