Bay Heating & Air Conditioning has been servicing the heating and air conditioning needs of Westlake OH since 1944.
Air Conditioning Repairs & Air Conditioner Replacements, Heating Repairs & Furnace Replacements and much more!
Call us now at: 440-249-0500 or check out the reviews and testimonials from your neighbors, that make us the top rated service provider in Westlake OH.
for Westlake, OH
Our Reviews by City
Rego - Westlake, OH
Very good service
Kelly - Westlake, OH
Marty is a great technician and is always able to correctly identify the problem and knows how to get it fixed.
Szarek - Westlake, OH
Jason was friendly and professional. He was well informed and I was very pleased with his service.
Review for Jose
MestekVicki - Westlake, OH
Jose provides amazing and thorough services. I was very happy to see that he was the technician assigned to my condo.
Bay Heating evaluation
Ohio George - Westlake, OH
On time and excellent service.
Good Service Price ?
Hammon - Westlake, OH
FeliceNancy - Westlake, OH
Mackson - Westlake, OH
Good communication in scheduling. While using shoe covers is a great courtesy, I would suggest replacing with new ones frequently!
Shmelter - Westlake, OH
Would appreciate not sharing opinions of the furnace with tenants. Tenant was alarmed that tech told him furnace was “40 years old”
Very knowledgeable in explaining the problem
Bobal - Westlake, OH
Loves our dog!!!!! feel that he gives an honest answer
Horansky - Westlake, OH
Jose has been my requested technician for years. He has become a friend. He also does excellent work.
Grane - Westlake, OH
went right to job and got it done
Rego - Westlake, OH
Guys we’re great
VotypkaMary - Westlake, OH
Rego - Westlake, OH
Always Great service
No Heat. Found A Plug A #210Sg And #35Wp Replace And A Bad 100 Amp Bearker Owner Will Replace Breaker . Cycled Heatpump And Air Handler And Fan Power Humidifier Fine At This at Time.
No heat. Upon arrival I found the furnace was failing due to a bad heat exchanger. I found aldehydes present and flame disruption from the far left heat exchanger. Due to conditions Paul is scheduled to quote furnace replacement ASAP.
Found expansion tank full drain tank if water continues to leak valve will need replaced watts 335 inlet male thread outlet female thread
Clean flame sensor and burners and controls check all operating and safety controls checked blower and motor change customer supplied filter and water panel cycle furnace to check OK
john & jerry install of infinity 80 furnace
Found 24 V fuse blown remove and replace cycle to check OK
$119.95 Furnace Tuneup. Replace #35Wp, Feed Tube, , Ez-Flex #24. â€œFurnaceâ€ 4= T-Stat, 52 Ohms HSI, Flame Sensor, 2= Stage 90% Inducer, Electric, 1.5â€ & 3.5â€ W.C. Gas Valve, Drain Trap, V.S. Blower, 33* Outside, â€œHumidifierâ€ Hum-Stat, Bypass Damper Open, Scale Control Insert, Water Valve, Cycled Clean And Check.
I found the flame sensor was reading .4 - .9 miliamps. I removed,cleaned and tested at 6-5.1 miliamps.
Found condensate drain line clogged remove plug with vacuum cycle furnace and humidifier to check OK
Found furnace off on code 13 limit found gas pressure elevated at 3.8 in high fire lowered to 3.3 and increase blower speed by 15% at infinity control
$119.95 Furnace Tuneup. T-Stat, Spark Igniter, Flame Sensor, 80% Inducer, Electrical, 3.5â€ W.C. Gas Valve, Burner, #16x25x1 Air Filter, 7.5+370 Run Cap Blower Motor, 24* Outside, Cycled Unit Clean And Check.
Heating tune up. The coustomer is interested in indoor air quality products. The humidifier needs replacement.
$119.95 Furnace Tuneup. Replace Ez-Flex #16. T-Stat, Ohms HSI, Flame Sensor, 2-Stage 90% Inducer, Electrical, 1.5â€ & 3.5â€ W.C. Gas Valve, Burner, Drain Trap, V.S. Blower Motor, 31* Outside, Cycled Unit Clean And Check,
Unit is making noise. I found a blower motor with a bad bearing. I replaced the blower motor and cycled the furnace with proper operation.
Clear out nest. I found the flue pipe was blocked with the remains of a bird nest. I cleared it out and cycled the unit with prpoer operation.
Return and replace damper. Cycle to check ok.
Cleaned and checked both furnaces and humidifier. I changed the water panel. And both filters. Disinfected humidifier. Cleaned flame sensor. Checked ignitor. Cycled both furnaces. Systems are operating properly at this point.
We preformed tune ups on two rooftop units and one downflow furnace. We found a failed heat exchanger on the north rooftop unit and are quoting repair. The Dow flow furnace had a failed control board. We replaced and tested the unit with proper operation. All filters were replaced.
Found secondary heat exchanger leaking water unit must be replaced estimate scheduled 1/17/19 @8:30.
Furnace tuneup. Replaced filter. Checked igniter, flame sensor, burners, gas valve, blower, capacitor,safeties,controls, cabinet, trap,intake. Secured all connections, cycled from tstat, reset tstat.
Found condensate elbow leaking remove and replace cycle to check ok.
Humidifier will not stop running. Upon arrival I found that the low voltage wire going from the humidistat to the humidifier is shorted. The coustomer is comfortable with manually controlling it by unplugging it.
Found zone three damper bad 493.00 to repair #18487. Schedule for Wed. P.M.
Furnace Tune Up. I replaced dirty filter.