Bay Heating & Air Conditioning has been servicing the heating and air conditioning needs of North Royalton OH since 1944.
Call us now at: 440-249-0500 or check out the reviews and testimonials from your neighbors, that make us the top rated service provider in North Royalton OH.
for North Royalton, OH
Our Reviews by City
Water leaking. We found a blocked condensate drain and dirty filter. We cleared the drain with high pressure CO2 and flushed with water. We replaced the media filter. We washed out the condenser coil and checked electrical components and checked amp readings. 242 volts. Compressor 8.8 amps out of 16.7. Fan is .82 out of .94. Capacitor is at 58/4.81 out of 40/5 under load and 37.9 cold. System is in proper working order at this time.