Bay Heating & Air Conditioning has been servicing the heating and air conditioning needs of North Ridgeville OH since 1944.
Call us now at: 440-249-0500 or check out the reviews and testimonials from your neighbors, that make us the top rated service provider in North Ridgeville OH.
for North Ridgeville, OH
Our Reviews by City
Aquila - North Ridgeville, OH
diagnostic and service
VassilyKen - North Ridgeville, OH
Bay heating and cooing
Heckenberg - North Ridgeville, OH
Good service,very reliable.
Oswald - North Ridgeville, OH
Boose - North Ridgeville, OH
On time. Extremely professional.
Pfarr - North Ridgeville, OH
On time and very friendly service team
Sieving - North Ridgeville, OH
The technician knew exactly what had to be tested and checked, and he was done in about 30 minutes. He even washed off the AC screen which to my memory was never done before. Best part, no cost for replacement parts and good for another summer.
PaulSue - North Ridgeville, OH
Jose is great
Lamolinara - North Ridgeville, OH
David - North Ridgeville, OH
Joe - North Ridgeville, OH
Tech was well informed took time to explain what he was doing
Great Service , Explained maintance program , made you feel very comfortable.
Hejduk - North Ridgeville, OH
As always Bay lives up to Lynn's Standards and promise to take good care of the customer...
Horn - North Ridgeville, OH
Like the company
Horn - North Ridgeville, OH
Great Service and so thankful for honesty and especial service!
Brown - North Ridgeville, OH
Club Furnace And Humidifier Tuneup. Replace #20x25x4 Air Filter Suppled. â€œFurnaceâ€ T-Stat, 49 Ohms HSI, Flame Sensor, 2-Stage 90% Inducer Assembly, Drain Trap, 119* & 116-76=43* & 40* T-R, Electrical, V.S. Blower Motor, 68* Outside, â€œHumidifierâ€ Fan Power, Hum-Stat, Scale Control Insert, Drip Tray, Water Valve, Solenoid, Feed Tube, Drainline, Cycled Unit, Clean And Check.
Follow Up. Replace #20x25x4 Air Filter Suppled And Add 1lb Of R-22, No Super Seal, 77*-57*=20 D-T, Cycled Unit Fine At This Time.
No Cooling. Found A Plug #20x25x4 Air Filter, Owner Will Replace, 82* Outside, 72*-53*=19* D-T, Cycled R-22 Unit Fine At This Time.
Got budget of 4k it is a rental property bid it for 70k btu carrier and payne he went with Trane cuz its an 80k btu and thats what the house has. I said we can put in a 90k btu but he said that would be overkill. He also said that their price was lower right out of the gate.
Found system low on refrigerant advised due to age replacement should be considered customer selling home and Uninterested in replacement
No Cooling. Found A Bad Spade Replace Both, Cycled Unit Fine At This Time.
No cooling. We found failed capacitor. It was reading 0.2/24 out of 5/35. We replaced the capacitor and suction insulation. We cycled the system with proper operation. Due to age, condition and inefficiency I highly recommend replacement.
We found a melted wire on the capacitor. We replaced the capacitor and 3 wire connections We cycled the system with proper operation.
I found a failed capacitor. I replaced the capacitor and cycled the unit with proper operation.
$119.95 Each Furnace And A/C Tuneup.
No cooling. I found a failed dual capacitor. I tested and replaced the capacitor. I cycled the system with a 16 degree temp drop. I inspected the filters. The system is operating properly at this time.
Odor. I cycled the unit with proper operation. There were no burning odors when we checked. We inspected the filter. We cycled the system. Unit is ok.
A/C tune up and media filter replacement.
Checked thermostat. Checked filter. Change number for 13 filter supplied by customer. Flushed AC trap out with water. Checked capacitor. Checked contactor. Checked all electrical connections. Cleaned outdoor condensing coil with water. Cycled system to check. System is operating properly at this time. Thanks Brian.
Water leaking. I removed evaporator coil cover and found the evaporator drain pan has rotted away. Due to age and condition type of refrigerant I highly recommend replacement of the air-conditioning system. The rust has eaten through the drain pan completely. Modern evaporator coilâ€˜s are manufactured with plastic pans.
Air conditioning shows no signs of being low on refrigerant charge at this time. The customer had seen a news segment on adding refrigerant to your system because they are no longer making this refrigerant. I advise customer that at this time everything is OK when it comes time to add refrigerant we should think about replacing the equipment due to its age. At this point in time the condenser is 25 years old. I took a temp drop of 14 degrees at the register. System is operating properly at this time.
Went with Mitchells based on price
Found multiple wires chewed through, contactor was bad also. Fixed Wiredâ€™s and replaced contactor. Unit operational at this time. Unit is 22 yrs old recommend replacing in near future.
A/C tuneup complete, Changed run capacitor, flushed drain, filter was clean coustomer provided, hosed down condenser coil, checked compressor/contacter, all electrical connections are secure, cycled cooling with 12* temp drop. Thanks johnathan
A/C tuneup complete, replaced air filter, turned of fan power humidifier for the season, hosed down condenser coil, checked capacitor/compressor contacter, all electrical connections are secure, cycled cooling with 14* temp drop customer is satisfied with cooling. Thanks johnathan
Found bad capacitor and system low on charge. Replaced capacitor and added 2 lbs r 22. Cycled system to check. System is operating properly at this time. Thanks Brian
Check thermostat check blower motor check filter customer supply flush condensate drain. Supply air 57* return air 71*. Check disconnect check capacitor 35+5+370 Dual Run Cap. Cycle unit on to check compressor and fan motor working. Wash and clean condenser coil. Outdoor temperature is 75*. At times of dispatch unit is working.
T-Stat Not Working. Found A Bad Non Programmable T-Stat. Replace T-Stat Cycled Cooling & Heating Mode And Auto & On Mode, Cycled Unit Fine At This Time.
Found blown capacitor on outdoor unit. Replaced capacitor,unit operational.