Bay Heating & Air Conditioning has been servicing the heating and air conditioning needs of Lorain OH since 1944.
Call us now at: 440-249-0500 or check out the reviews and testimonials from your neighbors, that make us the top rated service provider in Lorain OH.
for Lorain, OH
Our Reviews by City
Great and helpful service
Horansky - Lorain, OH
Marty was able to solve the problem by having me do a few things to see if I could fix the problem and I did!
Clean burners flame sensor vestibule and controls check all operating and safety controls clean condensate trap check blower motor and filter fire furnace check OK unit 27 years old but found no problems
Change filters per agreement found kennel room unit with bad heat exchanger going off on flame rollout do to same. unit will need replaced or heat exchanger replaced at occupants request
Perform three rooftop cooling tune ops cleared condensate traps change filters check blowers and motors check contactors capacitors compressors and fans cycle each rooftop unit to check OK found no problems.
Unit making noise. Unit Wasnâ€™t making noise upon arrival. Hosed off condensing coil. Checked voltages, contactor, dual cap, fan, and compressor. All connections are secure. Replaced air filter. Ran cooling from tstat with proper operation at this time. Reset tstag
Change filters per agreement.
Found nothing wrong technician error
Troubleshooting over the phone.