Bay Heating & Air Conditioning has been servicing the heating and air conditioning needs of Lakewood OH since 1944.
Call us now at: 440-249-0500 or check out the reviews and testimonials from your neighbors, that make us the top rated service provider in Lakewood OH.
for Lakewood, OH
Our Reviews by City
Go above and beyond
Ahup - Lakewood, OH
Our furnace (put in by a flipper) was only two years old when it started to malfunction. Bay came in and worked overtime to get replacement parts, we ultimately replaced the whole unit but I cannot imagine many companies spending as much time talking me through all the options and trying to find me the best products for the best price possible. I will sing their praises to the moon.
Great service. Courteous and pleasant!
FlynnChris - Lakewood, OH
Appreciate the timely response
Rambasek - Lakewood, OH
Good honest opinion
Great as Always!!
Roch - Lakewood, OH
Jose does a wonderful job. He listens and answers all my questions. He provides great service.
Came out after normal business hours, great service
MIchael - Lakewood, OH
Jason came out after 10 p.m. and quickly diagnosed the problem. He had the part in his truck and was able to replace it. He is a very friendly person.
KrejciMissy - Lakewood, OH
all went well!
Great service! Careful not to track mud into the house.
FlynnChris - Lakewood, OH
Casteele - Lakewood, OH
Chris - Lakewood, OH
I was very pleased with both your phone representative and with your repairman. Very efficient, knowledgeable and courteous. I am so happy to do business with Bay Heating and will recommend you to anyone who needs you’re services. Ciao
Response from Bay Furnace:
Thank you so much for the feedback. We work very hard to provide the best service possible and appreciate your willingness to let others know about your experience with us!
Great job by Jose as usual
Clark - Lakewood, OH
Great job by Jose as usual
Roger - Lakewood, OH
He did an excellent job
Excellent & efficient
Tropf - Lakewood, OH
Great tune up, pet usual
Tropf - Lakewood, OH
Zbin - Lakewood, OH
Love the maintenance contract
Tim - Lakewood, OH
Dependable, clean, and efficient
$119.95 Furnace Tuneup. T-Stat, 50 Ohms HSI, Flame Sensor,90% Inducer, Electric, 3.5â€ W.C. Gas Valve, Drain Trap, Blower Motor, 33* Outside, Cycled Unit, Clean And Check. Ordering 90% Inducer On 1/21/2019.
Replace fuse in disconnect. I amped out the circuit ay 40 amps per leg. Unit is operating properly at this time.
Replace 5 zone valves. Bleed and cycle each zone to check, ok.
Found temperature rise to be high. I lowered the gas pressure and reduced temperature rise to within factory recommended setting. Cycled system operating properly at time. If problem reoccurs. Recommend replacing both furnaces.
Intermittent no heat. Upon arrival I found the furnace was operating. I recalled errors with the Carrier Infinity control and found a pattern of inducer faults. I tested the furnace and found not only was the inducer failing but the pressure switches were out of calibration as well. We were able to order the parts and replace the same day. I also cleaned the condensate trap and flame sensor while I was waiting for the parts. I replaced the defective parts and cycled the furnace with proper operation.
Upon arrival found inducer motor assembly to be making a noise. Also found humidifier to not be working properly. Humidifier is out dated one of the original models of Aprilaire . Recommend replacing humidifier. Also recommend replacing Induced draft motor assembly. Inducer motor failure is due to lack of maintenance. Recommend bay maintenance plan.
$119.95 Furnace Tuneup. T-Stat, 16 Ohms HSI, Flame Sensor, 2-Stage 90% Inducer, Electrical, 1.6â€ & 3.5â€ W.C. Gas Valve, Burner, Drain Trap, 10+370 Run Cap Blower Motor, 41* & Rain, Outside, â€œHumidifierâ€ Hum-Start, Bypass Damper Open, Electrical, #10Wp, Water Valve, Solenoid, Drainline, Cycled Unit Clean And Check.
Club Furnace Tuneup. 2=T-Stat, Zone System, 48 Ohms HSI, Flame Sensor, 2-Stage 90% Inducer, Electrical, 1.5â€ & 3.5â€ W.C. Gas Valve, Burner, Drain Trap, V.S. Blower Motor, 39* & Rain Outside, Cycled Unit Clean And Check.
Found powerheads will not fit existing zone valve bodies entire zone valves will need replaced suggest Honeywell zone valve to replace current Erie valves office will call with Price System will need drained and re-bled after valve replacement
Club Furnace And Humidifier Tuneup. Replace 10+440 Run Cap. â€œFurnaceâ€ T-Stat, 14 Ohms HSI, Flame Sensor, 80% Inducer, Electrical, 3.5â€ W.C. Gas Valve, Burner, #413Sg, Blower Motor, 38* Outside, GPS, â€œHumidifierâ€ Hum-Stat, Bypass Damper Open, Scale Control Insert And Drip Tray, Feed Tube And Nozzle, Electrical, Drainline, Cycled Unit Clean And Check.
system operating properly at this time.Clean electronica air cleaner with bleach and odor kill also clean condensate pump with bleach and odor Kill recommend customer switch from electronica air filter to media filter
Club Furnace And Humidifier Tuneup. Replace Ez-Flex #20 & #35Wp. â€œFurnaceâ€ T-Stat, 54 Ohms HSI, Flame Sensor, 2-Stage 80% Inducer, Electrical, 1.5â€ & 3.5â€ W.C. Gas Valve, Burner, 10+370 Run Cap Blower Motor, 43* Outside, â€œHumidifierâ€ Hum-Stat, Fan Power, Scale Control Insert And Drip Tray, Feed Tube, Electrical, Water Valve, Solenoid, Drainline, Cycled Unit Clean And Check.
Found a key in exchanger to be leaking where inducer motor heat exchanger and bass from blower motor meet. Good man has already okayed the warrantee of heat exchanger inducer motor and gasket. Sean has quoted $1688 for labor customer approved and will wait for scheduling got system to run as best as I could right now it is operating properly but still leaking
Found master bedroom floor heat, family room, and basement zone valves stuck was able to free up but basement zone stuck last year suggest replacing all five zone valve powerheads but only three needed at this time that had failed Office will call with Price and customer will make decision on how many zone valves she would like replaced. Erie zone valve power head only #0765c0055ta01
Club 2= Furnace And Humidifier Tuneup. Found Humidifier Not Instill To New Infinity T-Stat. Replace T-Stat, #410Sg & #201Sg, #35Wp & #10Wp. â€œ2=Furnaceâ€ T-Stat, 43 & 49 Ohms HSI, 2=Flame Sensor, 2-Stage 90% & 90% Inducer, Electrical, 1.5â€ 3.5â€ & 3.5â€ W.C. Gas Valve, Burner, 2= Drain Trap & 1=Pump, V.S & 7.5+370 Run Cap Blower Motor, 34* Outside, â€œ2=Humidifierâ€ 2= Hum-Stat, Scale Control Insert And Drip Tray, Feed Tube And Nozzle, Water Valve, Solenoid, Electrical, Drainline, Cycled Unit Clean And Check.
Furnace tuneup complete. Air filter is clean. Inspected and cleaned hsi, flame sensor, burners, inducer, blower, safeties, controls and cabinet. All electrical connections are secure. Cycled furnace from tstat with proper operation at this time. Temp rise 54
No heat. Turned on high voltage, gas valve, furnace gas shutoff and checked air filter and flushed condensate drain. Checked hsi and cleaned flame sensor. All electrical connections are secure. Replaced blower run cap that was outside operating limits. Cycled from tstat with ok operation at this time. Reset tstat.
No heat. Fond and documented completely plugged negative pressure port for pressure switch tubing. Cleared port and cycled 15x without incident. Unable to confirm bad smart valve diagnosed by previous company.
Furnace tuneups complete. Replaced both air filters and flushed condensate taps. Inspected and cleaned hsiâ€™s, flame sensors, burners, inducers, blowers, controls, safeties, and cabinets. All electrical connections are secure. Cycled both furnaces from tstats with proper operation at this time. Checked system faults and reset tstats. Recommend replacing air filter on basement furnace every 30-60 days. Customer notified.
Upstairs unit clean burners flame sensors vestibule and controls adjusted gas pressure check all operating and safety controls change filter fire furnace to check OK downstairs unit cleaned pilot burners heat exchanger vestibule and controls check all operating and safety controls check blower motor and filter fire furnace to check OK unit older but operating very well.
Furnace tuneup Complete. Air filter is clean. Removed and cleaned 3wire pilot. Inspected and cleaned burners, gas valve, controls, safeties, and cabinets. All electrical connections are secure. Cycled from tstat with ok operation at this time. Reset tstat.
Return and replace 120 V thermostat for greenhouse heater cycle to check OK
Furnace tuneup complete. Replaced air filter. Inspected and cleaned hsi, flame sensor, burners, inducer, safeties, controls, vlower and cabinet. All electrical connections are secure. Cycled furnace from tstat with ok operation at this time. Reset tstat. All SA open
Found thermostat connections bad tap on thermostat thermostat resume proper operation cycle several times to check OK