Bay Heating & Air Conditioning has been servicing the heating and air conditioning needs of Lakewood OH since 1944.
Call us now at: 440-249-0500 or check out the reviews and testimonials from your neighbors, that make us the top rated service provider in Lakewood OH.
for Lakewood, OH
Our Reviews by City
Kocsis - Lakewood, OH
Did what was expected.
These were some very talented gentleman, with great costume service, very neat and they cleaned up beutifully. I would highly recommend them if you n
Murgu - Lakewood, OH
I had a wonderful experience, they took the time to answer all of our question.
Great Service, Very Thorough
Michael - Lakewood, OH
The service tech was very thorough and took the time to explain what he did for the maintenance check.
Nice guy, great service
Stone - Lakewood, OH
BT - Lakewood, OH
Nothing but the best for honesty and integrity. This is the place to go for trustworthy service!
Great service! Careful not to track mud into the house.
FlynnChris - Lakewood, OH
Friendly and courteous. Careful not to step on plants near the AC unit.
Jennifer - Lakewood, OH
Jose was excellent. Took the time to explain my systems to me and what I can do to keep them clean. Very knowledgeable. I would recommend him to anyone.
Beyer - Lakewood, OH
Quick, great service!
Fortner - Lakewood, OH
Castele - Lakewood, OH
Great Service. Awesome Price.
Long - Lakewood, OH
Everything went well with no complaints.
Please stop emailing thanks
Stop - Lakewood, OH
Dzurko - Lakewood, OH
Go above and beyond
Ahup - Lakewood, OH
Our furnace (put in by a flipper) was only two years old when it started to malfunction. Bay came in and worked overtime to get replacement parts, we ultimately replaced the whole unit but I cannot imagine many companies spending as much time talking me through all the options and trying to find me the best products for the best price possible. I will sing their praises to the moon.
Great service. Courteous and pleasant!
FlynnChris - Lakewood, OH
No cooling. I found the condenser fan blade had broken apart. This caused the motor to burn out. We need to quote for motor and blade replacement.
Furnace tune up. System was cycled with proper operation.
Found 20 amp fuse blown check for shorts found on replace fuse cycle air-conditioner to check OK customer used cranky baby coupon from years ago with no expiration date
$119.95 Each Furnace And A/C Tuneup.
Clear condensate traps check blowers motors and filters clean condenser coilâ€˜s check contactors capacitors compressors and fans cycle each air-conditioner to check downstairs unit 29 years old replacement needs considered but operating well at this time. Other upstairs unit fine.
Found dead compressor. Office will schedule estimator to quote new equipment. Thanks Brian
System has been filled with refrigerant by multiple companies. They don't have the money in their budget for replacement. They mentioned that they could live without it. Their heat source is a boiler and their A/C is in a side wall attic in 3rd floor, but not a knee wall.
Had budget convo with Mike (Husband) did not want to spend over 8k to add A/C. Currently there is only furnace and open return.
Check thermostat check blower motor check filter customer supply flush condenser drain and check condensate pump working. Supply air 53* return air 67*. Check disconnect check capacitor 55+5+440 turbo run Cap. Cycle unit on to check compressor and fan motor working. Wash and clean condenser coil . Outdoor temperature is 72*. At times of dispatch unit is working.
Check thermostat check blower motor check filter customer supply flush condensate drain and check condensate pump working. Supply air 50* return air 70*. Check disconnect check capacitor 35+5+370. Cycle unit on to check compressor and fan motor working. Wash and clean condenser coil. Outdoor temperature is 81*. At time of dispatch unit is working.
Found unit completely out of refrigerant pressure test and found two fittings outside not flared flare fittings pressure test at 300 pounds for a half hour evacuate and recharge cycle, ok.
New/replacement estimate. **Sean**
Club A/C Tuneup. Replace 401Sg. T-Stat, 71*-55*=16* D-T, Drain Trap, Blower Motor, R-22, Disconnect, 2=30 Amps Fuse, Electrical, 35+5+370 Dual Run Cap, 77* Outside, Hose Down, Remove Leaves And Cottonwood, Cycled Unit, Clean And Check
Found thermostat acting irradic. Checked filter. Checked outdoor coil. Cycled system to check. Checked batteries. System is operating properly at this time. Thermostat is not. Thanks Brian
Customer said outdoor unit not working. Cycle unit on to check. Found that unit was not having high voltage. Found bad Fuse in disconnect. Replace Fuse and cycle unit on. At time of dispatch unit is working.
Jose had diagnosed a bad blower motor. I found the relay on the cooling side of the control board to be bad. System is old and definitely recommend getting replaced. Due to the high volume of calls I hardwire the black wire from the blower motor directly to the L1 power for continuous operation and temporary cooling. This system is operating properly at this time. We need to return either Brian or an estimator to give a quote on a new system as soon as possible. Iâ€™ll instruct customer to call the office after 9 AM Monday morning thanks Brian
No Cooling. Found a Bad 35+5+370 Dual Run Cap, Replace Cycled Unit Fine At This Time.
No Cooling. Found A Bad Blower On A 30+ Year Old Furnace Due To Age Recommed Replacing 80% Furnace & A/C Tuneup.
Duct repair not working as planned - needs re-route