Bay Heating & Air Conditioning has been servicing the heating and air conditioning needs of Lakewood OH since 1944.
Call us now at: 440-249-0500 or check out the reviews and testimonials from your neighbors, that make us the top rated service provider in Lakewood OH.
for Lakewood, OH
Our Reviews by City
Appreciate the timely response
Rambasek - Lakewood, OH
Good honest opinion
Great as Always!!
Roch - Lakewood, OH
Jose does a wonderful job. He listens and answers all my questions. He provides great service.
Came out after normal business hours, great service
MIchael - Lakewood, OH
Jason came out after 10 p.m. and quickly diagnosed the problem. He had the part in his truck and was able to replace it. He is a very friendly person.
KrejciMissy - Lakewood, OH
all went well!
Great service! Careful not to track mud into the house.
FlynnChris - Lakewood, OH
Casteele - Lakewood, OH
Chris - Lakewood, OH
I was very pleased with both your phone representative and with your repairman. Very efficient, knowledgeable and courteous. I am so happy to do business with Bay Heating and will recommend you to anyone who needs you’re services. Ciao
Response from Bay Furnace:
Thank you so much for the feedback. We work very hard to provide the best service possible and appreciate your willingness to let others know about your experience with us!
Great job by Jose as usual
Clark - Lakewood, OH
Great job by Jose as usual
Roger - Lakewood, OH
He did an excellent job
Excellent & efficient
Tropf - Lakewood, OH
Great tune up, pet usual
Tropf - Lakewood, OH
Zbin - Lakewood, OH
Love the maintenance contract
Tim - Lakewood, OH
Dependable, clean, and efficient
Jose does a great job!!! Big thanks
Anderson - Lakewood, OH
Furnace Tune-Up w/Jose 12/28/16
Jennings - Lakewood, OH
Fantastic service from Jose, as usual. Prompt arrival and always top-notch professionalism. Very glad he did not stay with sales. He's the best service tech we've had.
System is 29 years old operating at approximately 60% efficiency. System is running properly at this time and in very good shape considering itâ€™s age
Boiler tune up. Pilot assembly was cleaned. Manifold gas pressure was checked. The pump was checked. Safetyâ€™s and connections were inspected. Boiler was cycled to 160*@26psig and back on at 130*@23psig. System is operating properly at this time.
Furnace and humidifier tuneups complete. Replaced air filter. Inspected and cleaned hsi, flame sensor, burners, inducer, blower, safeties, controls and cabinet. All electrical connections are secure. Ran furnace from tstat with ok operation at this time tstat reset. Humidifier cleaned cycled, water panel replaced, water flow adjusted and humidistat set.
I replaced the filltrol fill system and cycled the system with proper operation.
Boiler tuneup complete. Inspected and cleaned pilot assembly, gas valve, auto fill, burners, safeties, controls and burner box. All electrical connections are secure. Fired boiler from tstat with ok operation at this time. Customer reset tstat. WINTERIZED AC IN ATTIC. ANITFREEZE PLACED IN TRAP/DRAIN. CONDENSING UNIT COVERED AND DISCONNECT TURNED OFF. PUT CAPS IN DIFFICULT TO REACH S/A RUN OF UNICO SYSTEM PER CUSTOMER REQUEST.
Clean pilot burnerâ€™s fire box and controls check pump motor fill valve expansion tank and thermostat cycled boiler to check OK
Heating tune up.
Wrong parts. We need to reorder Andy reschedule.
Club Heatpump Tuneup. Replace #20x20x1 Air Filter Supplied. T-Stat, R410A, Electrical, R-Valve, Blower Motor, 46* Outside, 45 Amps, Cycled Unit Clean And Check.
Tuneups complete. Replaced air filter supplied by customer. Inspected and cleaned hsi, flame sensor, trap, burners, inducer, blower, controls, safeties, and cabinets. All connections are secure. Cycled furnace from tstat with proper operation at this time. Reset tstat. Humidifier cleaned, cycled, bypass opened, water panel checked and humidistat set.
Club Furnace And Humidifier Tuneup. Replace #35Wp. â€œFurnaceâ€ T-Stat, 15.6 Ohms H.S.I. Flame Sensor, 90% Inducer, Electrical, 3.5â€ W.C. Gas Valve, Burner, 20+370 Run Cap Blower Motor, Drain Trap, #201Sg, 61* & Rain Outside, â€œNew Bypass Humidifierâ€ Damper Open, Scale Control Insert, Drip Tray, Water Valve, Feed Tube, Electrical, Drainline,
Winterize 3rd floor ac drains, traps to prevent freezing.
Found smell to be from heat exchanger burning off Rust inhibitor used during storage and shipment cycle furnace to check after approximately another week or so of constant use smell will dissipate.
This is a 2 zone high efficiency boiler system. I found the system was operational upon arrival. I checked both zones for proper heating. There was a small amount of air in the third floor office radiator. The boiler cycled to 190* @ 29psig. This boiler also controls the domestic hot water. I could find no faults or failures at this time. The system is in proper working order.
No heat. I found the thermostat had failed. I was able to bypass to test the boiler. The boiler would fire however it was not filling to proper pressure. The system has a model 110 filltrol. I cleaned the inlet screen but it would not fill on itâ€™s own properly. I was able to manually fill to 12 psig and test the thermal cut out. Repair cost 16512 QSP $735.00
Club Furnace And Humidifier. Replace #10Wp. T-Stat, 3-Wire Spark Igniter, Electrical, 3.5â€ W.C. Gas Valve, Burner, #16x25x1 Air Filter, Blower Motor, 50* Outside, Cycled Unit Clean And Check. â€œHumidifierâ€ Hum-Stat, Bypass Damper, Scale Control Insert, Water Valve, Feed Tube, Electrical, Drainline, Cycled Unit Clean And Check.
I adjusted the fan limit control so it would turn off the blower. Unit is from 1986 with very poor ductwork. Unit should be replaced along with new ductwork ASAP.
Club Furnace Tuneup. T-Stat, 54 Ohms H.S.I. Flame Sensor, 2-Stage 90% Inducer, Electrical, 1.5â€ & 3.5â€ W.C. Gas Valve, Burner, Drain Trap & Pump, #16x25x1 Air Filter, V.S. Blower Motor, 52* Outside, Cycled Unit Clean And Check.
Found air conditioner that controls west side wing second and third floor not cooling. Tstat is located in west side of master bedroom. Reset tripped breaker. (Sub panel in the garage). Removed and replaced bad dual run capacitor and tightened all electrical connections. Cycled cooling with ok operation at this time. Tested both tstats that control master bedroom and both seem to be operating as designed.
Club Furnace Tuneup. Replace 4-Piece 80% Inducer Assembly. T-Stat, 71 Ohms H.S.I, Flame Sensor, 3.5â€ W.C. Gas Valve, Electrical, #401Sg, Burner, 7.5+370 Run Cap Blower Motor, 50* Outside, Cycled Unit Clean And Check.
Found plugged drain and dirty filter on first unit and performed furnace tuneup on downstairs unit cycled to check operation and replaced filter all okay at this time.
Clean pilot burners firebox and controls check all operating and safety controls blowdown boiler instruct customer of Same fire boiler to check OK unit older but operating very well.
Perform furnace tune up cycled to check all okay at this time.
Heating tuneups complete. Air filter is good until the spring. Inspected and cleaned hsi, flame sensor, condensate trap, burners, gas valve, controls, safeties, inducer blower and cabinets. Humidifier Cleaned, cycled, replaced water panel, opened bypass and and set humidistat to 35%. - clean pilot,burners,firebox and controls.check pump and expansion tank, vent damper and fired boiler to check. Bled air from system and tightened gate valve that was dripping. All systems ran from stats with proper operation at this time. Tstats reset.
Tuneups complete. Replaced air filter. Inspected and cleaned hsi, flame, sensor, burners, inducer, controls, safeties cabinets and blower. All electrical connections are secure. Cycled heat from tstat with ok operation at this time. OAT=93 degrees. Humidifier cleaned, cycled, water panel replaced, and customer to set humidistat when furnace is in use.