Bay Heating & Air Conditioning has been servicing the heating and air conditioning needs of Elyria OH since 1944.
Call us now at: 440-249-0500 or check out the reviews and testimonials from your neighbors, that make us the top rated service provider in Elyria OH.
for Elyria, OH
Our Reviews by City
Hickey - Elyria, OH
Bay Heating answered my emergency call and the on-call technician was here in good time. He assessed the heating unit from a number of different scenarios to identify the root problem. The part was ordered and will be installed today
Great people to solve problem
Bankson - Elyria, OH
I trust and depend on these people to find and solve any problems with the HVAC system.
Bankson - Elyria, OH
Jose came to do fall heat check. Excellent job.
Bay Heating Check up
Brian - Elyria, OH
Bay Heating performed a Check up on our heating system today. The Bay representative was great - very professional and knowledgeable and the work was done expertly and in a timely manner.Highly recommend Bay Heating.
Upon arrival we found a blown five amp fuse in the air handler. I replaced the fuse tested and cycled on emergency heat and it is working fine. We put the unit in heat pump mode and the unit failed at the thermostat. I manually cycled the heat pump and now it is operating properly. Due to the 20Â° outdoor temperature and recent power outages weâ€™re leaving the unit in emergency heat temporarily. The homeowners care taker is going to put the unit back into heat pump mode once the weather warms up.
Found bad control board. Replaced board. Cycled system operating properly at this time. Thanks Marty and Brian
Upon arrival I found furnace displaying code 23. Pressure switch did not open. No power to inducer due to faulty control board. I brought space heaters out for temporary heat until repair can be completed. Thanks Brian.
Found thermostat set for cooling turn to heat cycle to check OK
Clean pilot burners firebox and controls check all operating on safety controls check pump low-water cut off and water feed cycle boiler to check OK found no problems
Clean burners flame sensor vestibule and controls check all operating and safety controls check blower and motor change filter check all operating and safety controls fired furnace to check OK.
Found bad blower motor cust would like estimate scheduled for Tommorow.
Perform heating tune up 20 amps on each bank of electric strip heat cycled to check all okay at this time.
Check blower motor and filter change filter clear condensate trap check contactor capacitor compressor and fan cycle air conditioner to check OK
Found filter dirty remove and replace customer supplied cycle furnace to check OK reset limit switch
Check blower motor and filter clear condensate trap check contactor capacitor compressor and fan cycle air-conditioner to check 40Â° ambient clean condenser coil
Furnace and humidifier tune up