Bay Heating & Air Conditioning has been servicing the heating and air conditioning needs of Brecksville OH since 1944.
Call us now at: 440-249-0500 or check out the reviews and testimonials from your neighbors, that make us the top rated service provider in Brecksville OH.
for Brecksville, OH
Our Reviews by City
Ahola - Brecksville, OH
Smith - Brecksville, OH
Love Bay Furnace
Elizabeth - Brecksville, OH
Great visit. Able to do the furnace tune ups and make a repair in the same visit. Love that they were able to get the part to the tech while he did the tune ups.
We replaced 10=16x25x2 and 16=16x20x2 filters.
Found 20 amp fuse blown in main electrical disconnect panel remove and replace with customer supplied cycled unit to check check amp draw all three phases of 460 V service 1.8 A under full load each leg cycle rooftop in heating to check OK.
Completed furnace tune ups Changed all filters. Systems operating properly at this time
Rooftop unit in question was unit number one unit operating on arrival cycled to check regular maintenance scheduled for January 3, 2019 found no operational problems
Found unit number six fuse blown remove and replaced with customer supplied cycle rooftop six to check OK
Club Furnace And Humidifier Tuneup. Replace #10Wp. T-Stat, 46 Ohms H.S.I, Flame Sensor, 1.5â€ & 3.5â€ W.C. Gas Valve, Burner, Electrical, Drain Trap, Infinity Air Filter, V.S. Blower Motor, U.V. Light, 78* Outside, Cycled Unit Clean And Check.
Change rooftop filters per agreement size used in Pinned notes.
Found flare nut loose at cassett unit tighten and check with 300 lbs nitrogen for 45 minutes. Flare nuts need checked for proper ft lbs. before evacuation and recharge. Unit still has nitrogen holding charge. Will return tomorrow for final repair by install dept.
No cooling. I talked to the contractor that is installing a finished drywall ceiling around the Mitsubishi head. He told me that when he squeezed the refrigerant lines the refrigerant leaked out. Due to the need to access the unit drywall will block all ability to service the drain and other connections. We will need to quote for another style of head unit for the system. Paul will be out to quote. Contact is Dongwei Diag; 440-740-5057
Club 1=AC Tuneup. Replace 35+5+440 Dual Run Cap Old Unit . T-Stat, GAPCCCAR2025 Air Filter, Drain Trap, 71*-55*=16*D-T, V.S. Blower Motor, Bypass Humidifier Turn & Damper Close, R410A, Disconnect, Electrical, 76*Outside, Hose Down, Remove Cottonwood, Hose Down, Cycled Unit Clean & Check.
Perform 10 roof top cooling tuneups change all filters check blowers motors and belts check contactors capacitors compressors and fans cycle each air conditioner to check found bad run capacitor for blower motor unit three cycle each to check OK
Found 20 amp fuse blown. Check for shorts none. Replace fuse and cycle to check ok.
Commercial Maintenance COMFILT - $0.00 10-16x25x2 16- 16x20x2 change filters per agreement
Furnace and humidifier tuneup
2= Furnace tuneup & Replace Inducer assembly.