Bay Heating & Air Conditioning has been servicing the heating and air conditioning needs of Amherst OH since 1944.
Call us now at: 440-249-0500 or check out the reviews and testimonials from your neighbors, that make us the top rated service provider in Amherst OH.
for Amherst, OH
Our Reviews by City
May - Amherst, OH
Jason was very friendly and polite. He took the time to explain all that he was doing as well as sharing future options! Great work!
Commercial maintenance Replaced filters Checked burners, inducer, blower. Checked tension on blower belt. Ok
Phase I & II - 92% Single-stage Furnace & AC
Comtune complete. Replaced both air filters. Inspected and cleaned spark ignition, flame sensor, burners, gas valve, inducer, blower, belt, run caps, safeties, controls and cabinet. Replaced cracked blower drive belt and cycled with ok operation at this time from tstat. Reset tstat to the way it was found. Had to go get belt at part store. Tuneup and filter change $178 new belt $58. Poor cell reception on my end.
T/S not working. Upon arrival I found the thermostat was working properly. However the program was not correct. I programmed the cooling for 9:00 am to 9:00 pm 69* and 9:00 pm to 9:00am 74*. Due to high electric bill I changed the fan mode from on to automatic. For the weekend I programmed 9:00am to 6:00 pm 69*. The temperature was 69* when I arrived and cooling properly. Thermostat is a Braeburn.
Clear condensate trap check blower belt and motor change filters check contactor capacitor's compressor and fan cycle air conditioner to check OK